MINERAL OIL ISN’T YOUR ONLY OPTION
Mineral oil has long been the transformer liquid standard. However, natural ester liquid, a vegetable-based dielectric fluid, has been in use for decades and is becoming more common. Accepted industry-wide and in compliance with IEEE and IEC standards, natural esters can be used in power and distribution transformers, as well as certain substation equipment.
Improve fire protection, reliability, and the environment
Originally considered desirable for their environment-friendly characteristics, natural esters are now associated with performance benefits as well. Natural esters like the soybean-derived FR3® liquid offer higher fire and flash points to ease insurance challenges and has served as a substitute for fire suppression systems—even in indoor applications. FR3® liquids may in some cases provide natural self-drying properties that help reduce the moisture in your transformer’s insulating paper, extending its reliable life.
How do natural esters compare to mineral oil?
While natural esters offer some clear advantages, they also come with a few considerations. For instance, natural esters are not suitable for arcing equipment such as LTCs or for any free-breathing equipment due to the likelihood that contact with oxygen and heat will increase the liquid’s viscosity over time. It’s best to evaluate your specific application’s needs before choosing a transformer liquid.
Safe, compliant retrofilling services
If you determine natural esters are the right fit for your power needs, SDMyers can assist with retrofilling, including vacuum filling services. Our industry-leading team of highly trained field technicians follows clearly defined safety and quality control protocols supported by the liquid manufacturers and by current available IEEE standards. Additionally, liquid providers and other technical sources recommend changing the gaskets at the time of retrofilling, as well as potentially updating nameplates and labeling with a “K” rating. Our team is on hand to help with these related tasks.
Testing and diagnostics for natural esters
Natural esters do not require the same test packages as mineral oil samples and partnering with a laboratory that understands these distinctions is essential. For example, SDMyers does not recommend dissolved metals analysis or particle counts for natural esters. While dissolved gas analysis (DGA) can still offer important condition data on natural esters, SDMyers adjusts the limits for certain gases.